Grounding metal boxes on GFCI circut
On Apr 26, 7:39*pm, Red Green wrote:
Here;s a situation I came across.
I know any time a metal mounting box is used for a duplex outlet the box
should be tied to the ground wire coming in.
What if the metal box/outlet is on the load side of an upstream GFCI?
Maybe codes say it still has to be grounded (?) but from a safety
standpoint is it pointless to ground the metal box?
Metal boxes should always be "grounded".